PIPE DIAMETERS: 18"+ (450 mm)Cast-A-Seal 802 meets or exceeds:
Cast-A-Seal 802 is a cast-in, boot connector for larger pipes (18″ +) in concrete structures with straight walls.
It may be used for almost any application – sanitary or stormwater. The connector can be manufactured to fit almost any pipe diameter and can be cast-in with easily fabricated rolled steel ring mandrels or Styrofoam.
Features and Benefits
How It Works
|TYPICAL TEST RESULTS for CAST-A-SEAL 802 (as in ASTM C 923 and C 1478)|
|Test||ASTM Test Method||Test Requirements||Typical Result|
ACID and 1N
|D 534, AT 22ºC FOR|
|NO WEIGHT LOSS|
NO WEIGHT LOSS
|TENSILE STRENGTH||D 412||1200 PSI, MIN.||2100 PSI|
|D 412||350%, MIN||525%|
|HARDNESS||D 2240 (SHORE A|
|±5 FROM THE|
|D 573, 70± 1ºC|
FOR 7 DAYS
|DECREASE OF 15%,|
MAX. OF ORIGINAL
TENSILE STRENGTH, DECREASE
OF 20%, MAX.
|COMPRESSION TEST||D 395, METHOD B,|
AT 70ºC FOR 22 HRS
|DECREASE OF 25%,|
MAX. OF ORIGINAL DEFLECTION
|WATER ABSORPTION||D 471 IMMERSE 0.75|
IN DISTILLED WATER
AT 70ºC FOR 48 hrs
|INCREASE OF 10%,|
MAX. OR ORIGINAL BY
|OZONE RESISTANCE||D 1171||RATING 0||PASS|
|D 746||NO FRACTURE AT -40ºC||PASS|
|TEAR RESISTANCE||D 624, METHOD B||200 LBF/IN. (MIN.)||450 LBF/IN|
A flexible pipe-to-manhole connector shall be employed in the connection of the sanitary and storm drain sewer pipe to precast manholes or other structures. The connector shall be CAST-A-SEAL® 802 as manufactured by Press-Seal Corporation, Fort Wayne, Indiana, or approved equal. The connector shall be the sole element relied on to assure a flexible, watertight seal of the pipe to manhole. The connector shall consist of a rubber gasket and two external take-up clamps.
The rubber gasket element shall be constructed solely of synthetic or natural rubber, and shall meet or exceed the requirements of ASTM C923. The connector casting mandrel system shall include a precisely-formed opening in the concrete for installation of a replacement connector in the event that the cast-in connector is damaged.
The external take-up clamp shall be constructed of Series 300 non-magnetic stainless steel and shall utilize no welds in its construction. The clamp shall be installed by torquing the adjusting screw using a torque-setting wrench available from the connector manufacturer.
Selection of the proper size connector for the structure and pipe requirement, and installation thereof, shall be in strict conformance with the recommendations of the connector manufacturer. Any dead end pipe stubs installed in connectors shall be restrained from movement per ASTM C923.
The finished connection shall provide sealing to 13 psi (minimum) and shall accommodate deflection of the pipe to 7 degrees (minimum) without loss of seal.
Vacuum testing shall be conducted in strict conformance with ASTM C1244 prior to back fill. Other testing shall be conducted in strict conformance with the requirements of the connector manufacturer.